The choice of swimming pool circulating water pump should meet the following requirements:
(1) The rated flow of the pump should not be less than the calculated circulating water flow of the pool water purification treatment system to ensure the required flow rate of the pool water cycle;
(2) The lift of the pump shall not be less than the calculated value of the geometric height of the water supply, the resistance of the circulating purification treatment system equipment and the piping system, and the required outflow head of the pool inlet multiplied by 1.10;
(3) The pump should be a special frequency conversion speed regulating pump for swimming pool with high efficiency, energy-saving, corrosion resistance, and low noise;
(4) The circulating water pump of the pressure filter should not be less than 2 sets, and the standby pump should be set up and can be alternately operated with the working pump;
(5) The backwashing water pump of the quartz sand filter should be designed in parallel with the working model of the pool water circulating pump working pump and the standby pump, and adjust the circulating water pump working condition according to the flow and head check required for the backwashing of a single filter. Parameter.
Fuan Zhongzhi Pump Co., Ltd
registered the trademark "ZOZHI."
Add:No.155 Shangcun Qinxiyang Industry Zone,Fuan city,Fujian,China
Tel:+86 0593 6532656 Fax: +86 0593 6531158
Mobile: +86.137.0604.0131 E-mail: email@example.com