If the Generator AVR fails, its performance is:
1. The generator does not generate electricity.
2. the generator terminal voltage fluctuations of 20% and can not be adjusted.
3. The voltage at the generator terminal suddenly rises (above 500V).
The easiest way to judge is to separate the positive and negative (marked) excitation of the AVR cable from the AVR.
The positive electrode of the battery (12V) of the generator set is connected to the positive pole of the excitation machine, and the negative pole is connected to the negative pole of the excitation machine. After the battery is connected, the diesel engine is turned on.
If the generator's terminal voltage is balanced in three phases and reaches the rated value, the AVR is damaged.
If the generator's terminal voltage is balanced by three phases but lower than the rated value, there is a problem with the excitation and rectification of the generator.
Fuan Zhongzhi Pump Co., Ltd
registered the trademark "ZOZHI."
Add:No.155 Shangcun Qinxiyang Industry Zone,Fuan city,Fujian,China
Tel:+86 0593 6532656 Fax: +86 0593 6531158
Contact Person: Ms. Semmy Wu